The Cyber-Spy.Com Usenet Archive Feeds Directly
From The Open And Publicly Available Newsgroup
This Group And Thousands Of Others Are Available
On Most IS NNTP News Servers On Port 119.
Cyber-Spy.Com Is NOT Responsible For Any Topic,
Opinions Or Content Posted To This Or Any Other
Newsgroup. This Web Archive Of The Newsgroup And
Posts Are For Informational Purposes Only.
From: Richard VanHouten
Subject: Re: (Avionics) How can this circuit produce an "inductive surge"?
Date: Thu, 03 Oct 2002 08:33:08 -0400
Organization: Posted via Supernews, http://www.supernews.com
X-Mailer: Mozilla 4.76 [en] (Win95; U)
References: <email@example.com> <firstname.lastname@example.org> <_F1l9.30$VI5.email@example.com> <firstname.lastname@example.org> <email@example.com> <firstname.lastname@example.org> <email@example.com> <firstname.lastname@example.org> <email@example.com> <firstname.lastname@example.org> <email@example.com> <3D9A879F.CF98EE43@citlink.net> <3D9BB29C.6759F301@citlink.net>
Peter Gottlieb wrote:
> "Richard VanHouten" wrote in message
> > >
> > > Well, that makes some sense. But running a frequency converting MG set
> > > a UPS is not an optimal solution - why not just make the UPS run at the
> > > target frequency? The magnetics at 400 Hz are much lighter and
> > > than those required for 60 Hz, and the higher frequency makes other
> > > practical (eg, resonant).
> > The original product was the MG set (an import from Anton Piller Gmbh in
> > Germany), the front end inverter was our own design. IBM was
> > recommending the Piller MG sets for powering their then-current design
> > mainframes, so designing a stand-alone 400 Hz UPS would probably have
> > hurt business. The front-end inverter was a stand-by UPS; the MG set
> > ran directly off of mains during normal operation. Also, the inverter
> > had no magnetics to speak of; the MG set provided the power
> > conditioning.
> I forget that sometimes the business aspects take precedence over the
> engineering aspects. That always struck me as being somehow wrong even
> though with my business background I understand it.
> Yes, I've seen some larger systems with minimal magnetics, which can be done
> relatively easily when the bus voltages are high enough. I suppose if you
> are relying on the MG magnetics to be closely coupled to the inverter it
> would be an "interesting" problem dealing with the direct and reflected
> dynamics of the thing.
We were absolutely relying on the MG magnetics to be closely coupled to
the inverter; the inverter mounted on top of the MG control cabinet, and
we were relying on the MG to commutate off the SCRs in the inverter.
A seperate stand-alone 20A or 40A battery charger (which did have
significant magnetics) was used to charge the batteries.
Go Back To The Cyber-Spy.Com
Usenet Web Archive Index Of
The sci.electronics.design Newsgroup