The Cyber-Spy.Com Usenet Archive Feeds Directly
From The Open And Publicly Available Newsgroup
This Group And Thousands Of Others Are Available
On Most IS NNTP News Servers On Port 119.
Cyber-Spy.Com Is NOT Responsible For Any Topic,
Opinions Or Content Posted To This Or Any Other
Newsgroup. This Web Archive Of The Newsgroup And
Posts Are For Informational Purposes Only.
From: Fred Bloggs
User-Agent: Mozilla/5.0 (Windows; U; Win 9x 4.90; en-US; rv:1.0.1) Gecko/20020823 Netscape/7.0
X-Accept-Language: en-us, en
Subject: Re: temporary fix: household electrical failiure
References: <3DC6807F.firstname.lastname@example.org> <email@example.com>
Date: Tue, 05 Nov 2002 13:19:58 GMT
NNTP-Posting-Date: Tue, 05 Nov 2002 05:19:58 PST
Organization: EarthLink Inc. -- http://www.EarthLink.net
Take off UrPants to reply wrote:
> Since the socket closest to the breaker box was out figured the break must be
> in the wall behind that stretch. I cheaked for loose wires at breaker and at
> the plug and I saw no evidence of one. So I ran a 20 amp wire from the wire nut
> off of which the the socket was wired to the neutral of the breaker box. Now
> everything in that side works.
> Barring any further warning from you guys I just have to make sure I am running
> the correct wire, and figure out how to run it through the 6 feet of wall
> between the breaker box and the plug without tearing apart my wall.
Line breaks within the wall are seriously bad news. This is a definite
fire hazard because of arcing. You should identify the exact cable,
solidly tape a new one to it, and pull it completely through the wall.
At 20 amps this will be 12 gauge wire. If this is not possible then use
a continuity meter to identify the exact cable, disconnect it
completely- both wires, and run a surface conduit drop to the outlet.
Go Back To The Cyber-Spy.Com
Usenet Web Archive Index Of
The sci.electronics.design Newsgroup